[Date Prev][Date Next][Thread Prev][Thread Next][Date Index][Thread Index]
ground question here...
Made a rather disturbing discovery the other day.
I'm putting in a workbench (maybe this weekend?), and have a 240v drop
right over where it's to go. I was going to run that into a panel and give
myself a few 15A 120v breakers. But I found that the "genius" that wired
the garage ran 2 hots and used the bare copper wire as the ground & neutral.
Not good. I can pull 120v from either hot to the ground/neutral, but will
that be a "safe" ground for the variac or other stuff? I truly hate gettin'